Just about every RVer has a few power adapters, often referred to as “dogbones,” to make sure that they can connect to whatever power is available to them–this post will go over which power adapter types are safe to use, and which ones you might want to carry.
The job of a circuit breaker or fuse is to protect the downstream wiring from overloading and short circuits. Any wire configuration has a current rating, and a circuit breaker typically protects that wire.
Keeping that in mind, when we adapt an RV with a 50-amp plug (NEMA 14-50P) to either a 30-amp or 15-amp receptacle, the circuit breaker at the source will shut off power the wire’s limit is reached. At worst, under one of these configurations, we experience a nuisance pedestal breaker trip:
- 50-amp RV cord plugged into 30-amp, 20-amp, or 15-amp receptacle
- 30-amp RV cord plugged into 20-amp or 15-amp receptacle
For any of these configurations, you can find a UL-listed power adapter, and operate your RV safely.
But the other way doesn’t work. Let’s say you have something you want to power with a normal 15-amp plug. That includes a patio light, a heated hose, space heater or a string of flamingo awning lights. Now suppose you don’t have a 15-amp receptacle on the pedestal, or that you have something else plugged in.
Can you adapt down from a 50-amp or 30-amp receptacle on the pedestal to one for your 15-amp appliance? NO. If there was a problem with the appliance, or its cord, you could easily melt it before the breaker is overloaded enough to trip.
Note that in any of these situations, and even when plugging your RV directly into a pedestal, a receptacle in poor condition is still a hazard. A loose connection can easily generate enough heat to melt your plug or start a fire without tripping a breaker. If a plug goes in with little resistance, the receptacle probably needs replaced.
Power Adapters that are Safe to Use
All of these power adapters will have a smaller, lower amperage plug (male blades) on one end, and a larger/higher-amperage receptacle (female terminals). Look for UL-listed versions of these adapters, preferably with rigid grab handles.
50-amp RV plugged into 30-amp source
Power adapter has 50-amp female receptacle (NEMA 14-50R) and 30-amp male plug (NEMA TT-30P)
50-amp RV plugged into 15-amp source
Power adapter has 50-amp female receptacle (NEMA 14-50R) and 15-amp male plug (NEMA 5-15P)
30-amp RV plugged into 15-amp source
Power adapter has 30-amp female receptacle (NEMA TT-30R) and 15-amp male plug (NEMA 5-15P)
I’d advise avoiding this last type, just because of the mechanical strain it will create in most situations:
Don’t use these Adapters
These adapters allow for the connection of a smaller cord to a larger source. The cord in this situation could be overloaded without a breaker tripping, which is a safety hazard. These devices cannot be UL-listed.
30-amp RV plugged into 50-amp source
Power adapter has 30-amp female receptacle (NEMA TT-30R) and 50-amp male plug (NEMA 14-50R) DO NOT USE!
15-amp RV/device plugged into 30-amp source
Power adapter has 15-amp female receptacle (NEMA 5-15R) and 30-amp male plug (NEMA TT-30R) DO NOT USE!
50-amp Receptacle plugged into 30-amp and 15/20-amp source
First of all, these adapters won’t work on any receptacle that’s protected by GFCI. Any 15 or 20-amp receptacle installed since the 1970s is required to be protected by GFCI. It either doesn’t work, or it does and you’re working off of electrical service that’s old enough to have concerns of its own.
Any combination of 15-amp and 30-amp receptacles plugged into 50-amp source
Power adapter shown has 15-amp female receptacle (NEMA 5-15R) and 30-amp female receptacle (NEMA TT-30R) that are split from a 50-amp (NEMA 14-50P) plug. The bigger issue is that you have a 15-amp or 30-amp receptacle protected by a 50-amp breaker. Also, if you look closely, the handle for unplugging is a thin rubber strap that hooks on to the sides–that style isn’t very easy to unplug, and they’ll break, usually long before the plug itself needs retired. DO NOT USE!
Differences between RV Plugs and Common Household Plugs
Perhaps the most confused RV plug is the 30-amp TT-30, which looks very similar to the common 3-wire clothes dryer plug (10-30) which was installed in homes built prior to 1994. The two plugs are physically different in the center pin, but more importantly, they’re wired differently. The dryer plug supplies 240V, with a ground-neutral bond. This bonding means that the ground–which is designed to be a safety feature–is also current-carrying, which negates that function under certain conditions. The National Electric Code prohibited that practice in new home construction beginning in 1994, and a 4-wire plug has been used since then.
If having an electrician install a 30-amp service for an RV, make sure that it’s a TT-30 configuration, and that it’s properly wired to supply 120V with separate ground and neutral.
Which brings us to another plug, the RV 50-amp plug, which is a NEMA 14-50. This plug is commonly found on electric ranges, and is similar to–but different from–the typical dryer, which uses a NEMA 14-30. The 30-amp dryer plug has an L-shaped neutral, whereas the 50-amp RV plug has a straight blade. While not common, it would be safe to plug a 50-amp RV into a 30-amp 4-wire dryer receptacle, but not a 30-amp RV into a 50-amp range receptacle.
Is there a way to plug a 30-amp RV into a 50-amp pedestal?
Yes, but it’s not a product that you can just go out and buy. Do do it safely, you’d need a short cord sized for 50-amp service into a subpanel with a 30-amp breaker. If enough of you are interested, we might build one up to show the process.
Ok. Enough already! I’m a new RVer–what power adapter should I carry with me?
Each of these adapters have a rigid, molded grab handle, and have the plug at the proper orientation so that the cord and plug aren’t strained when hanging. Identify which type of RV you have based on the plug images below.
If you have a 50-amp RV, it should have a plug like this:
In that case, you can plug in anywhere (50-amp, 30-amp, and 15-amp receptacles) with these two adapters:
If you have a 30-amp RV, your plug will look like this:
And you’d just need this one power adapter: